|API 650 tank shell growth/rotation|
Posted by: 7004 ® |
Author Profile Mail author Edit
API Standard 650 9th Edition (Addendum 3 December 1996)
We intend to install the upper middle and lower sampling points on Jet A-1 product storage tanks connected to common header at ground level and further to Oily Water sewer.
This requires 03 Nos ¾” nozzles in tanks shell at different elevations (heights). Refer to section 22.214.171.124 openings near the bottom of tank shell will tend to rotate ……… To locate the bottom sampling nozzle out side the rotation area i.e I want to keep value of W (refer to Appendix P, P.3 Nomenclature & P.5.1), unrestrained radial growth of shell in inches =0 so that I can calculate the value of L, vertical distance form the opening centreline to tank bottom, in inches, I referred to Appendix-P and have following queries:Refer to Appendix P-Allowable loads on tank shell openings P.3 Nomenclature:
1. ∆T= Normal operating temperature minus installation temperature, in degree Fahrenheit
Would you further elaborate the Normal operating temperature and installation temperature? 2. How values of Modulus of Elasticity and Thermal Expansion Coefficient given in Table P-1 cover all the materials as these properties vary from material to material.
3. Any suggestions about small bore pipe (3/4” dia) supports attached to tank shell nozzles
|Post Reply | Recommend | Alert||Rate|
Powered by Engineers Edge
© Copyright 2000 - 2018, by Engineers Edge, LLC All rights reserved. Disclaimer