|Mechanical Design, Manufacturing and Engineering Forum|
] [ Search
] [ Engineering
and Design Database ] [ Resume/Job
Database ] [ Product
and Services Directory ]
[ Engineering, Design and Drafting Store ] [ Engineering Forum ] [ DFM DFA Training and Trainers ] [ GD&T Training GD&T Trainers ] [ Advertise ]
|[ POSTING POLICY / RULES ][ Archive#1 ] [ Archive #2 ] [ Archive #3] [ Calculators ] [ Tell A Friend ]|
|Forum Moderators: randykimball, Administrator|
Posted by: khaldoun ® |
Author Profile Mail author Edit
I have designed a conditioning system consists of four aeroterms each one is of 8 RT capacity (total 32 RT)the main connected pipes to the aeroterms is of 3" diameter the pump has the following data:H(8.5-16mH2O) water flow(300-1000L/min).
then a branch from the main pipe has been taken to feed two heatexchangers of 20RT now the 3" pipe is not adequate to cover the total capacity which is 52RT ,what to do in this case ,as amatter of fact I don't prefer to change the pipes ,is't possible to choose a larger pump to cover this lack in capacity or to add a new pump to the old one and whether to connect it in aparalal posision or consequent posision .
thanks in advanced.
|Post Reply | Recommend | Alert|
Powered by Engineers Edge
© Copyright 2000 - 2018, by Engineers Edge, LLC All rights reserved. Disclaimer