Power Conditioner Review
Power Conditioner Review
A power conditioner, also known as a line conditioner, is a device that is installed between an electronic system, module, or piece of equipment (such as a computer) and its power source (usually an AC wall outlet). The power conditioner features protection against power surges as well as provides a continuous voltage to the primary system during momentary and/or temporary voltage dips/reductions (such as those that would occur during a brownout). Power conditioners can also include EMI filtering capability and the ability to "smooth out" the inherent rhythmic cycling of typical AC.
Arguably one of the most popular types of power conditioners is the Constant Voltage Transformer, or CVT (also known as a Ferroresonant Transformer). This type of power conditioner is an excellent solution for equipment or loads that are meeting critical requirements (such as hospital equipment, computer systems, process control and automation, high end audio/video equipment and systems (such as home theater), remote sites, as well as third world applications). Just as importantly, a power conditioner will allow for the avoidance of brownouts, power sags and power surges - this avoids damage to critical systems that might be readily apparent or not. In the latter case, equipment life can be shortened by the previously mentioned power problems - and this may not happen until weeks or months later. The size and specifications of the power conditioner required depend on the system, equipment or device that is being protected. Besides the CVT, other types of power conditioners include Electronic Voltage Regulator, and Mechanical Voltage Regulator styles.
As mentioned above, power conditioners are utilized where brownouts, power sags and surges will interrupt the operation of critical equipment and/or damage electronic devices, modules, or systems. Applications include marine, medical, telecommunications, utility generation/distribution, railway, airport guidance and control as well as military systems. Depending on the application, power conditioners come in sizes ranging from a one-pound box with multiple outlets on the front of the enclosure, to rack-style cabinet units complete with a distribution panel and internal diagnostics.
Types od Power Conditioners
An AC power conditioner is the typical power conditioner that provides "clean" AC power to sensitive electrical equipment. Usually this is used for home or office applications and has up to 10 or more receptacles or outlets and commonly provides surge protection as well as noise filtering.
'Power line conditioners take in power and modify it based on the requirements of the machinery to which they are connected. Attributes to be conditioned are measured with various devices, such as, Phasor measurement units. Voltage spikes are most common during electrical storms or malfunctions in the main power lines. The surge protector stops the flow of electricity from reaching a machine by shutting off the power source.
The term "Power Conditioning" has been difficult to define historically. However, with the advances in power technology and recognition by IEEE, NEMA, and other standards organizations, a new actual engineering definition has now been developed and accepted to provide an accurate depiction of this definition.
"Power Conditioning" is the ability to filter the AC line signal provided by the power company. "Power Regulation" is the ability to take a signal from the local power company, turn it into a DC signal that will run an oscillator, which generates a single frequency sine wave, determined by the local area needs, is fed to the input stage of power amplifier, and is then output as specified as the ideal voltage present at any standard wall outlet.
Design of Power Conditioners
A good quality power conditioner is designed with internal filter banks to isolate the individual power outlets or receptacles on the power conditioner. This eliminates interference or "cross-talk" between components. If the application will be a home theater system, the noise suppression rating listed in the technical specifications of the power conditioner will be very important. This rating is expressed in decibels (db). The higher the db rating, the better the noise suppression.
The power conditioner will also have a "joule" rating. A joule is a measurement of energy or heat required to sustain one watt for one second, known as a watt second. Since electrical surges are momentary spikes, the joule rating indicates how much electrical energy the suppressor can absorb at once before becoming damaged itself. The higher the joule rating, the greater the protection.
Power conditioners vary in function and size, generally according to their use. Some power conditioners provide minimal voltage regulation while others protect against six or more power quality problems. Units may be small enough to mount on a printed circuit board or large enough to protect an entire factory.
Small power conditioners are rated in volt-amperes (V·A) while larger units are rated in kilovolt-amperes (kV·A).
Ideally electric power would be supplied as a sine wave with the amplitude and frequency given by national standards (in the case of mains) or system specifications (in the case of a power feed not directly attached to the mains) with an impedance of zero ohms at all frequencies.
No real life power feed will ever meet this ideal. Deviations may include:
- Variations in the peak or RMS voltage are both important to different types of equipment.
- When the RMS voltage exceeds the nominal voltage by 10 to 80% for 0.5 cycle to 1 minute, the event is called a "swell".
- A "dip" (in British English) or a "sag" (in American English – the two terms are equivalent) is the opposite situation: the RMS voltage is below the nominal voltage by 10 to 90% for 0.5 cycle to 1 minute.
- Random or repetitive variations in the RMS voltage between 90 and 110% of nominal can produce a phenomenon known as "flicker" in lighting equipment. Flicker is the impression of unsteadiness of visual sensation induced by a light stimulus on the human eye. A precise definition of such a voltage fluctuations that produce flicker have been subject to ongoing debate in more than one scientific community for many years.
- Abrupt, very brief increases in voltage, called "spikes", "impulses", or "surges", generally caused by large inductive loads being turned off, or more severely by lightning.
- "Undervoltage" occurs when the nominal voltage drops below 90% for more than 1 minute. The term "brownout" in common usage has no formal definition but is commonly used to describe a reduction in system voltage by the utility or system operator to decrease demand or to increase system operating margins.
- "Overvoltage" occurs when the nominal voltage rises above 110% for more than 1 minute.
- Variations in the frequency
- Variations in the wave shape – usually described as harmonics
- Nonzero low-frequency impedance (when a load draws more power, the voltage drops)
- Nonzero high-frequency impedance (when a load demands a large amount of current, then stops demanding it suddenly, there will be a dip or spike in the voltage due to the inductances in the power supply line)