Related Resources: calculators
Wind Flow Through Opening Calculator
Flow Through Opening Caused by Wind Only Calculator
Aspects of wind that affect the ventilation rate include average speed, prevailing direction, seasonal and daily variation in speed and direction, terrain, and local obstructions such as nearby buildings, hills, trees, and shrubbery. Liddament (1988) reviewed the relevance of wind pressure as a driving mechanism. A multiflow path simulation model was developed and used to illustrate the effects of wind on air change rate.
The equation below shows the estimated rate of air forced through ventilation inlet openings by wind or can be used to determine the proper size of openings to produce given airflow rates:
Q = 88.0 Cv A U
Q = airflow rate, cfm
Cv = effectiveness of openings (Cv is assumed to be 0.5 to 0.6 for perpendicular winds and 0.25 to 0.35 for diagonal winds)
A = free area of inlet openings, ft2
U = wind speed, mph
88.0 = unit conversion factor
Air intakes should be placed in exterior high-pressure regions, and air reliefs should be placed in exterior low-pressure regions, but because of wind variations, these static locations will, at times, not be optimal. Other considerations include flow control when wind speed is high, and security. Air intakes should face directly into the prevailing wind. If they are not advantageously placed, flow will be less than that predicted by Equation (1); if intakes are unusually well placed, flow will be slightly more.
Desirable air relief locations are
- on the leeward side of the building directly opposite the intake;
- on the roof, in the low-pressure area caused by flow separation;
- on a side perpendicular to the windward face, where low-pressure areas occur;
- in a dormer on the leeward side; (5) in roof ventilators; or (6) by stacks.
- Flow Rate of Steam in Schedule 40 Pipe Tables
- HVAC Air Change Out Frequency (minutes) General recommendations for total volume of air change out for selected type indoor air spaces.
- HVAC Air Duct Flow Resistance Chart HVAC duct flow resistancechart. Friction in Inches of Water per 100 Feet Friction of Air in Straight Duct
- Pressure Drop Equivalent Length of Pipes and Fittings Pressure Drop Equivalent Length of Pipes and Fittings Screwed , turbulent ﬂflow only, equipment length in feet.
- Wind Driven Rain Load Review , Equation and Calculator - The load from rain, especially wind-driven rain, is the main reason for moisture-related building failure.
- Wind Loading on Fences and Hoarding's Premium membership required.
- Wind Loading Analysis Main Force Resisting System Excel Calculator Spreadsheet
Per ASCE 7-05 Code Method 2 for Enclosed or Partially Enclosed Buildings
Design Wind Load Case 4 from Figure 6-9
- Wind Loading Analysis Wall Components and Cladding Building any Height Excel Calculator Spreadsheet
- Wind Loading Analysis For Low Rise Building Excel Spreadsheet Calculator
- Wind Map US and Regional Basic Wind Speed Data Chart USA and regional wind data.
ASHRAE Handbook HVAC System and Equipment - 2012